All extinguishers examined and checked. One was due for discharge and refill, this was completed. Fire blanket inspected. All items were found be "in date". Work carried out on 4 October 2017 by Fire Protection Services of Southfleet. BAFE BS5306 inspection certificate received. Total cost £146.67.
All curtains checked. Runners, tapes etc rectified as necessary and all chekced for correct functioning. Beewax spray applied to tracks. High infra red heater projection angles checked and resecured as necessary.
The problems previously reported were fixed in mid April. The plumber found two sanitary items dumped in a cistern. This had caused damage that needed new parts at cost of of over £45. Plumbers get all the best jobs! Good job completed by Julian who did not make any labour charges.